The Status LED on the front of the SmartX devices changes color and flashes to indicate the status of the device.
The override switches on Central IO modules with manufacturing date earlier than 2021-W26 must be disabled to remove the risk of an improper output. To disable the override switches, update the Central IO module firmware to version 2.017 or later.
The I/O modules have the following status indicator LEDs on the front of the module:
The SmartX AS-P server is the successor to Automation Server, and offers several improvements such as enhanced processor performance, increased memory size, dual Ethernet ports, and high-speed USB interfaces. Like the Automation Server, the SmartX AS-P server is a Schneider Electric manufactured embedded device that generally serves as the lowest tier EcoStruxure BMS server within the EcoStruxure BMS. The SmartX server controls and supervises equipment, typically HVAC equipment. SmartX AS-P servers use I/O modules with connected field devices, such as sensors and actuators, to do that.
The DO-FA-12 I/O module is a 12-channel, Form A relay, digital output I/O module.
The DO-FC-8 I/O module is a digital output, Form C relay, 8-channel I/O module.
The AO-8 I/O module is an analog output, 8-channel I/O module.
The AO-V-8 I/O module is an analog output, 8-channel I/O module.
The UI-8/DO-FC-4 module combines 8 universal inputs and 4 digital Form C relay outputs.
The UI-8/AO-4 module combines 8 universal inputs and 4 analog outputs.