The output override function allows you to manually override outputs. This function can be used for testing, commissioning, and maintenance of equipment.
You install an MP-C Display module on the MP-C or IP-IO module to enable manual override control of the analog and digital outputs. The MP-C Display module cannot be removed.
Use the Pulse Period Configuration screen to configure a pulse period for a digital pulsed output or tristate pulsed output.
The Status LED on the front of the SmartX devices changes color and flashes to indicate the status of the device.
There are three LEDs on the front panel of the IP-IO module.
You can select the Feedback option to rate your experiences and provide detailed information on the Commission mobile application.
The wiring recommendations for the communication ports on the SmartX servers and SmartX IP Controller devices apply to wires and cables used for RS-485 communications, LonWorks communications, USB connections, Ethernet connections, and Sensor Bus connections. Always use the recommended cables and wires.
You use the keys on the override display to navigate the screens of the user interface and to select options on menus and lists.
You install an IP-IO module on a flat surface inside a cabinet to ensure that the device is securely fastened and to allow for sufficient ventilation.
The relay outputs support digital Form A point types. The Form A relays are designed for direct load applications.