Before you can do an I/O checkout on a DALI light, you must first perform a DALI discovery and associate the discovered physical lights with logical lights in the RP controller configuration. You then wink DALI lights in order to identify the light location when associating the physical light with the logical light output.
The output override function allows you to manually override outputs. This function can be used for testing, commissioning, and maintenance of equipment.
The IP-IO module comes in three models with different I/O point count and different I/O point types.
The IP-IO module provides I/O expansion to your HVAC application over BACnet/IP and can share their I/O resources across applications running in automation servers, BACnet/IP controllers, or third-party systems. The IP-IO module can be installed near facilities in the field, away from the automation server or the BACnet/IP controller.
The IP-IO module has a built-in power supply designed to accommodate 24 VAC at 50/60 Hz or 24 to 30 VDC input power.
Use the Home screen to get information on the MP-C or IP-IO module model name, BACnet ID, and TCP/IP configuration settings.
The IP-IO module can be installed on a DIN rail or other flat surface inside a cabinet. The device is recommended to be installed in a cabinet, unless local regulations allow an exception.
Part number: SXWMPCDSP10001