Part number: SXWMPCDSP10001
Part numbers: SXWIPIOAA1S001, SXWIPIOBA1S001, and SXWIPIOCA1S001
In addition to the MP controllers and the b3 and MNB families of BACnet MS/TP controllers, the EcoStruxure smoke control system also supports the proprietary Infinet i2 family of controllers when connected to the AS-P-SMK smoke control server. The AS-P-SMK and AS-P-NLS-SMK Servers provide integrated support for the Infinet i2 controllers and has been part of the UL864 system listing since evaluation in 2018.
The EcoStruxure smoke control system supports the MP controllers and IP-IO modules mentioned previously in this guide.
The tables that follow provide a summary of all the equipment models you can interconnect to form the smoke control system.
You must install most of the controls products listed here in an enclosure that meets the following minimum criteria. After the criteria, several specific enclosure models are listed as examples of enclosures that meet the minimum criteria you can use for the smoke control system.
Common network accessories include the following:
This following applicable documentation is useful for installing the BACnet smoke control system equipment.
The MP-C controller and IP-IO module, which are based on the same hardware platform, are installed using either of two methods: they can be snapped onto a DIN rail or screwed onto a flat surface inside a cabinet.