You can manually verify the direction of the damper rotation of a VAV controller to verify that the actuator rotates clockwise or counterclockwise to open.
In the Commission mobile application, in the Device List view, select the VAV controller to be checked.
Flow Balancers are automatically brought to the Verify rotation page after Flow Balancing is complete.
In the Menu , select Flow Balance .
In the Air Balancing menu, select Verify rotation .
To monitor the rotation in the Current Status pane, select the information icon
If an error message is displayed during rotation check, perform a manual check.
For more information, see Error Message is Displayed During Rotation Check of the VAV Controller .
Upon completing the manual checks, repeat steps 2 and 3.
The VAV controller's rotation direction to open the damper is manually verified. Next, on the Manual checkout view, you continue manual checkout as needed