You log on to the Commission mobile application to perform commissioning, flow balance, and checkout operations on BACnet/IP controllers.
You must configure a unique MS/TP address for the RP and MP controllers and RP-IO modules that only support MS/TP communications. You do so during installation by using position 1-7 on the address DIP switch.
You can reset and restart the IP-IO modules in different ways depending on how long you press the reset button. The resets and restarts can affect the retention of values after restart based on the retain levels configured for the variables.
Use the Operator Display Settings screen to configure Operator Display and perform administrative tasks.
Use the device detail screen to interact with the device and its features.
You display a list of downloadable objects to identify objects that must be synchronized.
You display a list of devices so that you can check the status, invalid or offline, of the devices in the system.
In a Timed Force Multistate object, you configure one or more state values to define a text string associated with each of those values.
SpaceLogic Sensors are a family of living space sensors designed for BACnet/IP controllers using the EcoStruxure Building Operation user interface. These sensors use an RJ-45 sensor bus that provides communication and power from the BACnet/IP controller.
You can reset and restart the RP controllers in different ways depending on how long you press the reset button. The resets and restarts can affect the retention of values after restart based on the retain levels configured for the variables.