This section provides recommendations on wire sizes and lengths for the IP-IO modules.
This section provides recommendations on minimum wire sizes (cross-sectional areas) and maximum wire lengths for the wires connected to the screw terminals of Central IO modules, AS-B servers, RP and MP controllers, and IP-IO modules. Recommendations on minimum wire size and maximum cable length for the digital inputs of the RP controller expansion modules, the DALI bus of the DALI light modules, the SMI Interface of the SMI blind modules, the Zigbee DALI and 0-10V modules, and the KNX Modbus gateway are also provided. The recommendations are for guidance only. Other wire sizes and lengths may be used, depending on wiring rules and when appropriate.
Part number: SXWMPCDSP10A01
Part numbers: SXWIPIOAA10A01, SXWIPIOBA10A01, and SXWIPIOCA10A01
The Status LED on the front of the automation devices changes color and flashes to indicate the status of the device.
There are three LEDs on the front panel of the IP-IO module.
Before you can do an I/O checkout on a DALI light, you must first perform a DALI discovery and associate the discovered physical lights with logical lights in the RP controller configuration. You then wink DALI lights in order to identify the light location when associating the physical light with the logical light output.
The IP-IO module comes in three models with different I/O point count and different I/O point types.
The IP-IO module has a built-in power supply designed to accommodate 24 VAC at 50/60 Hz or 24 to 30 VDC input power.