You can manually verify the direction of damper rotation to determine whether the actuator rotates clockwise or counterclockwise to open.
In the eCommission application, in the Device List view, select the MP-V controller to be checked.
The Device List view has filters that allow you to easily find and select the controller:
If you are logged in as a Flow Balancer, the device list is automatically filtered to show only MP-V controllers.
If you are logged in as a Technician, you can sort the list of discovered devices by controller model.
Tap Verify rotation in the Air Balancing menu and then follow the prompts.
To monitor the rotation in the Current Status pane, tap the information icon
If an error message is displayed during rotation check, perform a manual check.
For more information, see Error Message is Displayed During Rotation Check of MP-V Controller .
Upon completing the manual checks, repeat steps 2 and 3.
The MP-V controller's rotation direction to open the damper is manually verified. Next, on the Manual checkout view, you continue manual checkout as needed